Here’s a list of handy tips for the do-it-yourselfer or for those who just want to know what their system needs for the best possible performance. Just like your car, your home comfort system needs routine maintenance to keep it running at its best. Without regular servicing, heating and cooling systems waste energy and are more likely to break down. But with the proper attention, they can keep you comfortable year-round.
Below are some basic tips to keep your system running efficiently. However, these tips are not designed to replace annual servicing by a qualified service technician. Schedule an HVAC Service Appointment Online or Call (425) 827-9997
Heat pumps, furnaces, and boilers need a yearly professional tune-up.
Step 1 A close inspection will uncover leaks, soot, rust, rot, corroded electrical contacts and frayed wires. In furnace (forced-air) and boiler (hot-water) systems, the inspection should also cover the venting, ductwork or pipes, dampers or valves, blower or pump, registers or radiators, as well as every part of the furnace or boiler itself.
Step 2 Next, the system should be run through a full heating cycle to ensure that it has plenty of combustion air and chimney draft. Test the air for carbon monoxide.
Step 3 Finally, it’s time for the down and dirty task of cleaning the burner and heat exchanger to remove soot and other gunk that can impede smooth operation. For the burner, efficiency hinges on adjusting the flame to the right size and color, adjusting the flow of gas. A check of the heat pump should include an inspection of the compressor, fan, indoor and outdoor coils and refrigerant lines. Indoor and outdoor coils should be cleaned, and the refrigerant pressure should be checked.
Tuning up the distribution side of a forced-air system starts with the blower. The axle should be lubricated; blades cleaned and blower motor checked to insure the unit isn’t being overloaded. The fan belt should be adjusted so it deflects no more than an inch when pressed. Every accessible joint in the ductwork should be sealed with mastic or UL-approved duct tapes. Any ducts that run outside the heated space should be insulated. On a hot-water system, the expansion tank should be drained, the circulating pump cleaned and lubricated and air bled out of the radiators.
While thermostats rarely fail outright, they can degrade over time as mechanical parts stick or lose their calibration. Older units will send faulty signals if they’ve been knocked out of level or have dirty switches. To recalibrate an older unit, use a wrench to adjust the nut on the back of the mercury switch until it turns the system on and, using a room thermometer, set it to the correct temperature. Modern electronic thermostats, sealed at the factory to keep out dust and grime, rarely need adjusting. However, whether your thermostat is old or young, the hole where the thermostat wire comes through the wall needs to be caulked, or a draft could trick it into thinking the room is warmer or colder than it really is.
A neglected in-duct humidifier can breed mildew and bacteria, not to mention add too much moisture to a house. A common mistake with humidifiers is leaving them on after the heating season ends. Don’t forget to pull the plug, shut the water valve and drain the unit. A unit with a water reservoir should be drained and cleaned with white vinegar, a mix of one part chlorine bleach to eight parts water or muriatic acid. Mist-type humidifiers also require regular cleaning to remove mineral deposits.
Most houses with forced-air furnaces have a standard furnace filter made from loosely woven spun-glass fibers designed to keep it and its ductwork clean. Unfortunately, they don’t improve indoor air quality. That takes a media filter, which sits in between the main return duct and the blower cabinet. Made of a deeply pleated, paper-like material, media filters are at least seven times better than a standard filter at removing dust and other particles. An upgrade to a pleated media filter will cleanse the air of everything from insecticide dust to flu viruses. Compressed, media filters are usually no wider than six inches, but the pleated material can cover up to 75 square feet when stretched out. This increased area of filtration accounts for the filter’s long life, which can exceed two years. The only drawback to a media filter is its tight weave, which can restrict a furnace’s ability to blow air through the house. To insure a steady, strong airflow through the house, choose a filter that matches your blower’s capacity.